the wires coming off double pole will give you 240 volts,110 each the black and white hook to these,doesn`t matter which way,ground to ground
Ground is always ground, Black and white are your two "hots." You will need a dedicated circuit, you cannot run this off existing 120V wiring. A 15A 240V circuit should be more than sufficient. If this is a permanent instalation you can use 14/2 wire as you normally would, and wire it as you normally would with the exception of the 240V breaker. If you install switches, timers, etc. Make sure they are all rated for 240V. Remember, you can't just mix-and-match between 120 and 240V. 240 appliances will not run on 120 and 120 appliances will burn up on 240.
The Malibu 4-Light Black Metal Flood Kit are made up of Four 50 Watt floodlights.
the flood light is convex
the flash flood the flood light
You don't say "turn off" or turn on". Light should be connected black to black and white to white and ground to ground. If you connect white to ground it will work, but you are then using the ground wire for an unintended purpose. Neutral is bonded to Ground at the panel. Current on ground wire could cause ground loops and may cause GFCI to trip if you have them in your house.
The amperage of a flood light is governed by the wattage of the lamp.
Yes, the Malibu 4-Light Black Metal Flood Kit comes with bulbs Low Voltage kit.4-CL1, 50 watt floodlights,100 Ft. cable etc.
Red is positive black is ground.
Yes. Connect Black to Black, White to White and bare ground wires together.
There should be a black & white wire coming from the light. Hook black to black and white to white. Then connect the ground wire to the light chassis. You need 12/2 with ground for the circuit. You do not need a light fixture box for these type lights.
You put switch in series with the black supply wire and the black wire to the first light. Then connect black wire of first light to black wire of second light, black wire of second light to third light and so forth. Do the same with the white wires and ground wires.