Best Answer

It would depend almost entirely on what that room is USED for, i.e., the type of occupancy. If it is a storage room in a retail store, you are not allowed to have more than one person for each 300 sq ft (i.e., 5 people), but if it is a classroom in a K-12 education occupancy, you would be allowed one for each 20 sq ft of open space (net floorspace), i.e., 72 people.

The NFPA Life Safety Code, or other similar code adopted in your jurisdiction, will determine what load factors to use for your particular occupancy, whatever it is.

After you know the permissible load by area, you then calculate the permissible exit load, based upon the location, type and width of the various doors. If the exit load is smaller than the area load, your occupancy is limited by the exits.

Q: What is the occupancy load for a 1440 square foot room?

Write your answer...

Submit

Still have questions?

Continue Learning about Other Math

Net floorspace divided by load factor from occupancy tables of applicable code. For instance, NFPA 101 requires 7 sq ft per person in compact dance areas and 15 sq ft per person where there is seating, provided it is not fixed seating. You then calculate the egress load by allowing one person for each 0.2 inches of doorway or hallway (whichever is narrower), or 0.3 inches if there are stairs. The lower number (area load or egress load) is the overall limit for that occupancy. There are, however, many other factors for each specific location, such as whether the main doors can accommodate at least 2/3 of the max load, whether there are sprinklers, whether there is live entertainment, what floor of the building it's on, what kind of building structure it is, etc.

2

It means One (1) Twenty foot, full container load for a minimum order. What is 1x20? -- One twenty foot container FCL -- Full Container Load

It depends on what load is on the wall.

Please re-word your questions a little better. There is insufficient information to answer this question.

Related questions

To convert kilonewtons (kn) to occupancy load, you need to know the weight-bearing capacity of the floor. Occupancy load is typically measured in pounds per square foot or kilograms per square meter depending on the building code. Once you have the weight-bearing capacity of the floor, you can calculate the occupancy load by dividing the capacity by the force exerted by the kn.

square foot of what, concrete, wood or paper or what

square foot/feet

50 lbs

If you mean the maximum occupancy of a room, then several things are considered. The square footage of the room, the room's purpose, and the number of emergency exits that exist are factored in.

Divide the heat loss or gain obtained by the load calculation by square footage of the building.

The load for outlets supplying specific appliances is determined by calculating the power requirements of the appliance (in watts or amps) and ensuring that the outlet and electrical circuit can safely handle that demand. This involves considering factors such as voltage, current, and the anticipated usage of the appliance to prevent overloading the circuit. It's important to refer to the appliance's manual or consult an electrician to determine the correct load for each outlet.

it depends on the type of occupancy, and varies on the code that you want to use.

It is a "LIVE LOAD" which is the weight of snow for which a roof is designed for. It is usually 40 lbs. per square foot. Al dead load is the weight of the roof structure itself.

it depends on the type of occupancy, and varies on the code that you want to use.

What kind of elevators? Freight, Passenger or automobile lifts? All capacities are based on the square foot area inside the elevator.

If this pool is indoors consult your local fire marshal for the restrictions on the building occupancy level